Standards as High as Your Own
NECA Online Help Desk Please leave a message
When a sub-panel is installed in a residential dwelling, can the grounding electrode conductor consist of the rigid conduit raceway or need it be run inside the raceway with the other conductors?
Hey Gwyneth thanks for your question. The NEC doesn't use the term "sub-panel" although it is often used by electricians and others in the electrical industry. Rigid Metal Conduit cannot be used as a Grounding Electrode Conductor but one is not required for a Feeder supplied Panelboard if both are within a building such as a Dwelling Unit. You might be thinking about an Equipment Grounding Conductor, which is required, but Rigid Metal Conduit and several other metal raceways are allowed as equipment grounding conductors as stated in 250.118. A wire type equipment grounding conductor can also be installed inside metal raceways but it is not specifically required. All of the terms that are capitalized in this paragraph are defined in Article 100, except Rigid Metal Conduit is in 344.2, which can be reviewed for more information.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: firstname.lastname@example.org.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.