Standards as High as Your Own
NECA Online Help Desk Please leave a message
Hi and Peace to you, well there is always some installation practices that seem to arise. I have my thoughts on what the code says, really like to hear what you say the code states. Can one use a green THWN insulated equipment ground run with URD in a trench (direct buried) (feeder or even branch circuit) or even connected to a concrete encased electrode? What if the outer jacket is removed and only the bare copper wire is now exposed to the direct buried elements? I see 310.10 (F), 250.118&119,300.5 coming into play and maybe the white book. Will look forward to your code answers. Thanks.
Hey Butch thanks for your question, there are multiple possible answers. Conductors that are directly buried must be identified for that use as stated in 310.10(F). In general wire type equipment grounding conductors can be bare, covered or insulated as stated in 250.118(1). Bare aluminum equipment grounding conductors are not allowed to be in direct contact with masonry or the earth, or be terminated within 18 inches of the earth, as stated in 250.120(B). But that restriction does not apply to copper conductors. Similar rules for aluminum grounding electrode conductors are in 250.64(A). It is very common to use either bare or insulated copper grounding electrode conductors underground where connected to grounding electrodes. Bare copper conductors are also used as grounding electrodes in 250.52(A)(3) and 250.52(A)(4).
Equipment grounding conductors installed underground for agricultural buildings must be insulated as stated in 547.5(F). So, if not at an agricultural application then is seems copper equipment grounding conductors should not be an issue underground whether they are bare, covered or insulated. Make sure the AHJ agrees and there are no local restrictions. An exception to 310.10(F) that allows bare or covered wire type equipment grounding conductors underground would make the rules clearer in the future.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: firstname.lastname@example.org.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.