Standards as High as Your Own
NECA Online Help Desk Please leave a message
Do equipment grounds need to be larger than the individual ungrounded conductors in parallel installations if the overcurrent device is large enough to require a larger equipment ground? Another words, does the “in no case needs to be larger” statement in 250.122 refer to the individual ungrounded conductors or the total circular mill of the entire ungrounded conductors of each phase?
Hey Mike thanks for your question. Yes. Equipment grounding conductors are sized based on the overcurrent device as stated in 250.122(F). Conductors are allowed to be connected in parallel if they meet all the conditions in 310.10(H). That concept uses multiple current paths to equally share the total current for each phase or grounded conductor. The circuit conductors supplying the equipment is the total area of all the "individual conductors" that are connected in parallel.
Equipment grounding conductors, for a parallel arrangement, might need to be larger than any one of the individual ungrounded conductors but does not need to be larger than all of the ungrounded conductors (total of the multiple paths) of any one phase.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: firstname.lastname@example.org.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.