Standards as High as Your Own
NECA Online Help Desk Please leave a message
Charlie, Thank you for all of your great work to help the electrical industry.
My question concerns a 60 amp, three pole, four wire power receptacle that has been factory built into a fused disconnect switch. Typically, these receptacles and switches are rated at 600V. Am I prohibited from using one of these receptacle / fused disconnect assemblies in a 240V, three pole, four wire application?
Thank you, Robert Frye, PE
Hey Robert thanks for your question and the compliment. Electrical equipment must be rated for at least the nominal circuit voltage as stated in 110.4. Receptacles connected to circuits with different characterizes (such as different nominal voltages) must be designed to be noninterchangeable, on the same premises as stated in 406.4(F). So unless the listing instructions prohibit it and you are not using the same receptacle configuration for a different voltage the 600 volt switch/receptacle combination is allowed to be used for a 240 volt application.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: email@example.com.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.