Standards as High as Your Own
NECA Online Help Desk Please leave a message
Re: CQD answer published February 22 and March 4, 2019 -Flexible Cords
I had really hoped there would be many more comments and info regarding the difference between cable and cord. My personal overly-simplified impression and rule-of-thumb these days is that:
CABLE can be used to connect between components of a system (i.e. robotic arm sections, power supply to powered device, etc) but that only CORD (limited to the insulation types defined in Table 400.4) can touch the floor, and/or connect to bldg power (whether with a plug or hard-wired.)
Hey Perry thanks for your comments. Cable, raceway and other wiring methods must be secured and supported based on the specific XXX.30 section of the applicable article. But they are not prohibited from being on or contacting floors, they can actually be secured to and supported by floors.
Flexible cords can be used if necessary, for flexibility - such as portions of robots based on 400.10(9). Some judgment is necessary when determining what is acceptable based on the conditions.
As we previously said, from a simplistic view, cables are in Chapter 3 and flexible cords are in Article 400.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: email@example.com.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.