Standards as High as Your Own
NECA Online Help Desk Please leave a message
Re: CQD answer published Tuesday, February 13, 2017 -Terminal Ratings and Ampacity
I believe you have confused the issue on 90 Deg C. wire. In my 2017 code handbook, page 257, 310.15(A)(3) in the blue commentary under this section it states “Most terminations are designed for 60DegC and/or 75DegC maximum temperatures. The higher-rated ampacities for conductors of 90DegC, 105DegC, and so forth cannot be used unless the terminals at which the conductors terminate have comparable ratings. Your explanations of the adjustment factors is good, but unless the breaker terminals are rated at 90 DegC, you cannot use that column of the table, according to the above comment.
Hey Alton thanks for your comment and I often get confused. You are correct but the answer given is also correct. If there are no adjustment or correction factors to be applied then the values in the 60 degree C [for 100 amperes and less] and 75 degree columns [for over 100 amperes] of Table 310.15(B)(16) are what need to be used as maximums. But if conditions of use exist then the 90 degree C value can be used for applying adjustment and correction factors (formerly called derating) as stated in 110.14(C) if the insulation has that rating. If after applying the factors the value determined is lower than the 60 or 75 degree column values then it (the determined value) is the ampacity. If the ampacity determined by applying the factors results in a value that is higher the 60 or 75 degree column values then the 60 or 75 degree value is the limit. We don't get to "use" conductors at the 90 degree column values unless the terminations are listed and marked with that temperature rating but we do get to start from those values for applying the factors. The small word "IF" in the second paragraph of 310.15(B) helps explain this.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: email@example.com.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.