Standards as High as Your Own
NECA Online Help Desk Please leave a message
When you burry. Conduit underground what type of tape do you put on the conduit. You don t put C 130 do you or can you? But what is the tape you apply to the conduit?
Hey David thanks for your question. The NEC uses the word Approved, as that term is defined in Article 100 for describing various types of corrosion protection in 300.6. Compounds, coatings, and tapes are examples of types that can be used, the product you suggest is a rubber splicing tape, but manufacturers can give you information on what corrosion products they have. Reviewing the .10 and .12 sections in the Article for the specific raceway used can also give some guidance. What is considered suitable is often determined at the local level, based on soil makeup and soil resistance. In many areas steel rigid metal conduit is directly buried with no additional corrosion protection beyond that of the galvanizing. Field cut threads would also need corrosion protection as stated in 300.6(A).
NECA publishes the National Electrical Installation Standards (NEIS) which are a series of ANSI-approved performance and quality standards for electrical construction. NECA 101, Installing Steel Conduits, has information on corrosion protection in 4.6 including transitions from concrete to soil. NEIS can be purchased at:
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: firstname.lastname@example.org.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.