Standards as High as Your Own
NECA Online Help Desk Please leave a message
Question 1- Does a single receptacle, in a dwelling, for a septic alarm located in the basement next to the load center have to be on GFI?
Question 2- Does a duplex receptacle, in a dwelling, for a security alarm, with the upper receptacle tabs broken so not energized and the alarm transformer plugged into the lower receptacle and secured with the plate screw and located next to the load center have to be on GFI? It has been indicated by a residential home inspector that all basement receptacles have to be on GFI. Please advise asap. Thank you
Hey Russell thanks for your questions.
(1) Yes, if in an unfinished basement GFCI protection is required for 15 and 20 ampere 125 volt receptacles as stated in 210.8(A)(5)
(2) No, if supplying a permanently installed fire alarm or burglar alarm system GFCI protection is not required as stated in the exception to 210.8(A)(5). GFCI protection is specifically prohibited for fire alarm systems as stated in 760.41(B) and 760.121(B).
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: email@example.com.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.