Standards as High as Your Own
NECA Online Help Desk Please leave a message
NEC 300.14 clarification - ac conductors enter Fronius snapINverters and terminate on terminal blocks. Do the conductors coming into the inverter need to be 6 inches long? I believe the inverter is a device and 300.14 applies but I am being told that ac wiring inside the inverter does not apply.
Hey William thanks for your question. Section 300.14 applies to outlet, junction and switch points and requires 6 inches of free conductors. Conductors that are in integral part of equipment do not need to comply with that rule as stated in 300.1(B). Usually the manufacturer's instructions will provide sufficient detail for conductor terminations especially part of listed equipment. Inverters for use with PV systems must be listed as stated in 690.4(B). If the termination point of the field installed conductors in the inverter is considered an outlet as defined in Article 100 then the 6 inch minimum dimension applies. Even if it does not apply, providing sufficient conductor length for future servicing and maintenance is a good idea.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: email@example.com.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.