Standards as High as Your Own
NECA Online Help Desk Please leave a message
My boss has to put in about 20 Handicap lifts with seats, so people with handicaps can enjoy the pool too. There will be one for each pool, they are 12 volt DC battery powered lifts. To recharge the battery for the lifts they must be recharged on a special charger and there is no way for a 120 AC to get near the lift chair. There is one #10 bare continuous ground wire run from the chair base all the way to the Square D breaker panel ground terminal, about 70 feet. My question is, wouldn't it be better to have a ground rod as close as possible to the chair base and run the ground to that and not the breaker panel. As it is you have a path from the breaker panel to the pool chair via the ground wire and anything can happen to make that ground wire hot. If the ground is not in the breaker panel then there is no chance for the ground wire to pick up any voltage. So to me this seems to be a lot safer way.
Hey Paul thanks for your question. Electrically powered pool lifts must be listed, labeled and identified for swimming pool and spa use as stated in 680.81. The instructions included with them must be followed as stated in 110.3(B). Also electrically powered pool lifts must be bonded using the rules in 680.26(B)(5) and (B)(7) as stated in 680.83. Notice that an 8AWG or larger bonding conductor does not have to be run to remote panelboards, service equipment or electrodes as stated in the last sentence of 680.26(B). But equipment grounding conductors, if required must provide an effective ground fault current path to the electrical supply source.
Equipotential bonding is installed to reduce voltage gradients in the pool area, not to provide a "ground". The wording in 250.4 might help explain the performance requirements of grounding and bonding.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: email@example.com.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.