Standards as High as Your Own
NECA Online Help Desk Please leave a message
Re: CQD answer published Friday, October 26, 2018 -Flexible Cord Above Ceilings 2
In addition, Refer to NEC-2011 Article 400.12(5), where Installing a flexible cord above a ceiling in itself is not prohibited, any “permanently installed” plug-in equipment using a flexible cord, with or without a cord cap as its power source connection is prohibited. Thusly, a receptacle mounted above the ceiling for use on a “permanently mounted” piece of equipment, such as a projector, emergency battery lighting unit, etc. would also be prohibited. Attached is an older illustration, referencing the 2005 or 2011 NEC, but in our opinion, this still stands.
Edward M. Grafe
Hey Edward thanks for your comment. As we explained in the previous answer flexible cords, including power supply cords (usually with attachment plugs) are not allowed (they are prohibited) above suspended or dropped ceilings as stated in 400.12(5). Although this is still a little confusing, flexible cords that are allowed for a specific application in 400.10 (such as for portable equipment) are not allowed if they are prohibited for a specific application in 400.12 (such as above a suspended ceiling).
An exception was added to 400.12 in the 2014 NEC that allows flexible cords within enclosures that are suitable for other environmental air spaces by 300,22(C)(3). For example, plug in type power supplies with flexible cords can be used above suspended or dropped ceilings - if they are within those types of enclosures but not if they are in the "open".
There is no specific rule that prohibits receptacles from being installed above suspended or dropped ceilings. It becomes a violation when the flexible cord exists there. Projector mounting equipment (can be motorized) is available with a metal enclosure that is recessed in a suspended ceiling. Or a receptacle outlet can be installed facing down in the suspended ceiling so the entire length of flexible cord is not above the ceiling.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: firstname.lastname@example.org.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.