Standards as High as Your Own
NECA Online Help Desk Please leave a message
What is the recommended practice of grounding and bonding a 480/277V generator that serves (2) 4 pole automatic transfer switches and 1 three pole automatic transfer switch? The three pole ATS is fed from a 480V to 208/120V transformer. In this case would it be permissible to locate the system bonding jumper at the generator? Do you foresee an issue with objectionable ground currents on the system? Thank you for your time.
Hey Nick thanks for your question. The NEC does not provide recommendations and sometimes there are choices. Alternating current systems must be grounded as stated in 250.20(B). The choice of transfer switches can determine whether the system is separately derived or not as that term is defined in Article 100. Some prefer to switch the grounded conductor if one is used and others prefer to directly connect the grounded conductor from different systems together.
If the system (generator in your case) is a separately derived system a system bonding jumper must be installed at a single point as stated in 250.30(A)(1) and locating it at the generator is allowed. The system grounded conductor is not allowed to be "re-grounded" on the load side of the system bonding jumper as stated in 250.30(A). Systems installed this way reduce or eliminate objectionable current because they are only connected to ground once thereby not providing parallel paths for current.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: email@example.com.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.