Standards as High as Your Own
NECA Online Help Desk Please leave a message
When doing a dwelling unit calculation, article 220.50 for motors will send you to 430.24, 430.25, 430.26. with these article you are to incorporate 25% of the largest motor. I have found different code calculation practice strategies in which some say if the A/C is omitted per 220.60 you would not use the A/C as the largest motor. Usually the A/C is the largest motor in a house calculation, could you tell me which would be the correct way to calculate this and where to find it in the code if you are to not use the A/C if omitted from the calculation. The way I read it the A/C motor is still installed on the service feeder so it should be able to be used as the largest motor.
Thank you, Markco
Hey Markco thanks for your question. Those sections are not very well correlated and there likely are some inconsistent practices being done. If the AC is not the larger load, and is omitted as stated in 220.60, it is somewhat logical that it does not get used to apply the 125% as the largest motor. There is no wording that says you can omit it for one calculation but need to apply it in another. Keep in mind that the 125 % will be included in the branch circuit calculation as 220.60 only applies to the total load of a feeder or service.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: firstname.lastname@example.org.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.