Standards as High as Your Own
NECA Online Help Desk Please leave a message
Re: CQD answer published Wednesday, January 10, 2018 -Multiwire Branch Circuit
Thanks to all of the numerous readers that sent in comments regarding the question about circuit breakers in position 32 and 36 using a "shared" neutral. The reply answer did not get published so we are trying again.
You are correct and thanks for pointing that out. A simultaneous means of disconnecting all of the ungrounded conductors is required as stated 210.4(B) which the answer pointed out. But the ungrounded conductors must be supplied from different phases to be a multiwire branch circuit as stated in the definition of Branch Circuit, Multiwire in Article 100. There must be a voltage between the ungrounded conductors or the neutral current would be the total of both ungrounded conductors in a single-phase system which is likely the case in the example provided. So besides the circuit breakers having to be next to each other so that a simultaneous means of disconnect can be provided they need to be next to each other so that the grounded conductor (neutral in this case) is not overloaded.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: email@example.com.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.