Standards as High as Your Own
NECA Online Help Desk Please leave a message
Re: CQD answer published Wed, December 19, 2018 -Meter Disconnect Switches
"Charlie" no need to publish my comments but it seems Carl the questioner is mixing apples and oranges. The cold sequencing switch is indeed required in NJ for certain size services but I am not sure it has to have an AIC rating since it is a non-fused switch. The disconnect that is immediately after the meter socket is the one that is a fused switch (or it could actually be a circuit breaker if someone desired that) and that is the one which requires the AIC rating. Also the grounding electrodes and grounding electrode conductors do not appear until the main disconnect is reached. There are no grounding conductors to be installed in the cold sequencing switch. The cold sequencing switch is strictly a safety to be used by the utility to allow their employees to remove and install the meters while not under load. Another point is that the cold sequencing switch is bonded by the neutral or ungrounded conductor similar to the meter socket or CT cabinet bonding. Looking forward t tomorrows response. Keep up the good work and Merry Christmas to all.
Rich Van Wert
Rich thanks for your follow up comment and compliment. Meter disconnect switches are allowed on the supply side of the service disconnect as stated in 230.82(3). But they must have a short-circuit current rating (SCCR), as that term is defined in Article 100, at least that of the available short circuit current as stated in that section. True, the switches can be installed to help utility personnel do their work in a safer manner, but they are often part of premises wiring as that term is defined in Article 100 because they are on the load side of the service point, also defined in Article 100. As the submitter mentioned non-fusible enclosed switches are not available with SCCR's above 10 kA so if the available fault current exceeds that, the switch would need to be a fusible type to achieve that rating. See 110.9 and 110.10 for additional information.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: firstname.lastname@example.org.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.