Standards as High as Your Own
NECA Online Help Desk Please leave a message
If I used a length of 1-inch aluminum rigid conduit (10-foot sleeve) for physical protection of a grounding electrode conductor installed on a wall, is bonding required from the contained grounding electrode conductor to the conduit at both ends where the conductor enters the sleeve and where it exits?
Thanks for any clarification you can provide.
Bonding from the grounding electrode conductor to both ends of the raceway is required by the NEC. Aluminum conduit is not a ferrous metal raceway which is what the requirements in Section 250.64(E)(1) applies to. The requirement could also be satisfied using Schedule 80 PVC conduit, if the type of construction allows for that.
ABOUT CQD: The Code Question of the Day (CQD) is NECA and ELECTRICAL CONTRACTOR Magazine’s flagship National Electrical Code (NEC®) public forum for the industry, sponsored by EATON. The daily distribution of Q&A generates a lively dialogue and shares relative Code-based practical responses.
SUBMIT YOUR CODE QUESTION: Click here to submit a question to for inclusion in an upcoming edition of the Code Question of the Day, or email firstname.lastname@example.org.
CHARLIE TROUT: Charles M. Trout, better known as Charlie, was a nationally recognized NEC® expert and author. He served on several NEC technical committees and is past chairman of CMP-12. In 2006, Charlie was awarded NECA’s prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development and technical training. NECA continues to provide this public forum in memory and recognition of all his fine contributions that has made the NEC what it is today.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. NEIS can be purchased in the NECA Store in three formats: a printed or PDF download of a standard or, as an annual subscription service.
NECA SAFETY PRODUCTS & PUBLICATIONS: NECA produces electrical safety publications and products for the industry including jobsite safety guides, handbooks and resource kits. View a full listing of available resources and products »
IMPORTANT NOTICE: Unless the question requests a response based on a specific edition, all answers are based on the latest edition of NFPA 70® National Electrical Code®.
This correspondence is not a formal interpretation of the NEC® and any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, the NEC Correlating Committee any Code-making panel or other electrical technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
UPDATE YOUR SUBSCRIPTION PREFERENCES: Subscribe or Unsubscribe from this list.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.